Are you ready to read the shortest blog post ever answering a very common question about mobile diagnostic imaging equipment? If not, take a minute, brace yourself, and pop a couple Dramamine. We don’t want to hurt anyone. If you are ready: let’s do this!
What are the power requirements for mobile diagnostic imaging trailers?
3-Phase/480 volts fits most. Most mobiles across the larger modalities (MRI, CT scanner, PET/CT, Cath/Angio) are set up with a trailer-to-building hook up with Russell Stoll-style connectors and adapters.
If you still have concerns about your power hook-ups, please contact us. Our project managers will be sure to ask all the right questions to help you make sure your power and connections are configured correctly.
Wow! Did that just happen?